If you’re responsible for tracking energy use, you may have wondered about the impact of weather on your facility energy use. The good news is that if you have access to your utility bills, you don’t have to wonder any more. You can determine the impact of weather.
Only two variables are necessary to perform this mathematical calculation:
The energy use figure is available from your monthly utility bill. And thanks to the wonders of modern technology, the weather severity information is available for free on the internet.
EnergyCAP energy management software uses a simple linear regression model to calculate weather sensitivity, but you can do the same thing by plotting the monthly consumption data vs. the total number of heating or cooling degree days for the same time period in a spreadsheet.
The approach can be visualized as a plot of the utility bills (dependent variable) for each calendar year, month-by-month, on a grid with consumption on the vertical axis and weather (the independent variable, as expressed using the “degree days” concept) on the horizontal axis. Here’s how it looks:
Consider this raw plotted data from an electric meter in the winter. The X-axis is heating degree days and the Y-axis is energy used:
Each point represents an electric bill received in a winter month. The “best fit” line is found by statistical simple linear regression analysis, and is called the “regression line.”
For the charted data above, it is easy to see that the regression line would be horizontal. The meter uses about the same amount of electricity every month. This suggests that the meter is not weather-sensitive in winter, because the cold weather apparently has no effect on usage.
A line slope of “zero” means that the weather factor (amount of weather-related usage, expressed as KWH per degree day) would also be zero.
Consider this data from a gas meter in winter. This graph is very different. As the regression line makes clear, the usage increases as the weather gets colder, and decreases as the weather gets milder. Clearly, this meter is weather sensitive.
At the point of zero heating degrees (mild weather), the usage is zero. This means that the meter has no base load. There is no non-weather sensitive usage. All of the energy used is related to the weather. Let’s look at one more example:
This winter utility data from an electric meter shows a consistent slope which rises to the right, so the meter is weather sensitive. In the cold months such as December, January, and February, the weather load (expressed as heating degree days) is greater, while in the mild months the weather load is smaller.
Note, however, that unlike the previous example, the Y-intercept (the point at which the regression line meets the vertical axis) has a value greater than zero, in this case about 5,000 KWH. The Y-intercept reveals the meter’s base load—the non-weather-related portion of the total usage. This meter uses 5,000 KWH even if there is mild weather (zero heating need degrees), plus some additional KWH depending on the weather.
Once you understand the weather sensitivity of your meters/buildings, you’re in a better position to anticipate weather-related expenses. You’re also in a better position to more accurately compare energy use from year to year, since it becomes possible to normalize year-to-year comparisons for weather. This enables you to obtain a more complete picture of the effectiveness of energy management initiatives.